Online Trade Magazine Alternative Energy from Solar, Wind, Biomass, Fuel Cells and more…
If you do not have an AltEnergyMag partner account, please register - it's free! S-Jet Solar Wire
Solar PV systems consist of many components, which are connected by cables and connectors. This is one of the main safety hazards of any solar PV system. In this Solis article we'll share how a connectivity failure could create a security problem and how to prevent it.
Solar PV systems consist of many components, which are connected by cables and bespoke connectors. This is one of the main safety hazards of any solar PV system. In this Solis seminar we'll share how a connectivity failure could create a security problem and how to prevent it.
According to actual O&M data from 746 PV plants, the EU Horizon 2020 "Solar Bankability" project team gave a list of the TOP 20 technical failures in PV plants. "Wrong/Absent Cable Connection" and "Broken/Burnt Connectors", ranked in the top two on the list of failures.
In addition, Fraunhofer ISE research also shows that the root cause of PV system failure is mainly concentrated in poor contact caused by installation problems.
Connection is the general way to form a complete electrical system. In a PV system, there are many connection points. Taking a 30kW three-phase PV system as an example, which uses 100 x 300W modules and a 30kW string inverter; the configuration is as follows
The number of DC connection points for a single string is 21 (See Figure 2 below), and there is a total of 105 connection points for 5 PV strings. In addition, there are 24 AC connection points, so overall the system has a total of 129 connection points.
The larger the system, the more connection points. Adding MLPE devices to the original system triples the number of connection points. In Figure 3 below, only an optimizer is added, and the connection points of the string are increased by 40.
In PV systems, improper wiring or incorrect use of cables will result in poor contact and increase in contact resistance. This affects system performance, increases system costs, can cause additional losses and create hidden system hazards.
Select correct and high-quality materials, including the selection of DC and AC cables; the selection and configuration of system connectors, circuit breakers, etc. require strict attention in the early design stage.
Ensure the installation specification conforms with the relevant electrical standard and use professional wiring tools. You should refer to the installation manual of each product for guidance.
Regularly use a thermal imager to troubleshoot system connection problems, or use the SolisCloud online monitoring platform to perform operation and maintenance inspections to repair faults in a timely manner.
Connection failure is a very serious safety hazard in PV systems. Issues can cause both damage to the system but also reduce the impact of any energy savings factored in at the feasibility stage.
We need to pay attention to installation and construction and later O&M to avoid these problems and improve system safety.
Utilizing online monitoring software such as SolisCloud ensures that any faults can be identified and fixed quickly to avoid costly system downtime.
Ginlong's cost-effective solutions for residential, commercial, and utility-scale users deliver value at every level of the solar supply chain, engaging both homeowners and businesses, as well as power producers and renewable energy investors across the globe. Presented under the Solis brand, the company's solar inverter product line uses innovative string technology to deliver first-class reliability, validated under the most stringent international certifications. Combining a global supply chain with world-class R&D and manufacturing capabilities, Ginlong optimizes its Solis inverters for each regional market, servicing and supporting its customers with its team of local experts.
This post does not have any comments. Be the first to leave a comment below.
You must be logged in before you can post a comment. Login now.
Hybrid Microgrid System Helps Company Meet Production and Sustainability Goals
Lessons Learned From Installing Battery Energy Storage Into an Existing PV Array
Measuring Solar Access Value (SAV) & Total Solar Resource Fraction (TSRF) With Accuracy
International EV Batteries 2022: Cost-Effective Engineering for Hybrid and Electric Vehicles
Reuters Events: Energy Transition North America 2022
Intersolar North America 2023 & Energy Storage North America
Subscribe | Search | Promote Products | Feature Your Company | Publish News | List Event
Articles | News | Stories | Products | Companies | Events
Twin Core Dc Solar Cable © 2010 - 2022 AltEnergyMag - All Rights Reserved Powered by BTH Management